Picture | Next Picture |
| Inspection Gallery
fixture was installed with the wrong type of wire. In this exterior
application, there should be conduit or proper exterior cable.
Many homes we inspect have handyman electrical wiring, especially in
garages, attics, basements, crawl spaces and exterior lighting.
The hole in the soffit is oversized and is a possible point of entry for pests.
was noted as a unprofessional electrical installation.
See our Homeowners Library for more valuable information